Crystal Blue Plumbing, Heating & Air provides heater and air conditioning repair, service, installation and services in Sacramento CA and surrounding areas. Check out what some of our customers are saying about Crystal Blue Plumbing, Heating & Air Plumbing, Heating and Air Conditioning services.
for Sacramento, CA
Exceptionally professional, competent and courteous
Dhillon - Sacramento, CA
Fast & Terrific
Marilyn - Sacramento, CA
Fast, detailed and efficient. He and his "sidekick" were so wonderful. I really want Crystal Blue Plumbing to hit the airwaves.!! Thank you, Marilyn
Marilyn - Sacramento, CA
My level of confidence with this company and Tom is high... friendly and understanding of being low income has it's challenge's.. Thanks so very much. Marilyn
Lauren - Sacramento, CA
Michael rocks! Very efficient, friendly and professional.
Job well done
Sammie - Sacramento, CA
Find Air Conditioning intermitent service
Robert - Sacramento, CA
Very through on investigating the the trouble and fully explained what he thought might be the problem
Tanya - Sacramento, CA
Knowledgable, courteous, and very helpful. Enjoyable experience. Thank you Michael, and for taking care of the snake on my patio!
Outstanding service, very professional
Kristin - Sacramento, CA
Kevin with Crystal Blue Plumbing was very professional and friendly. He was of such great service and took care of my requests quickly and was very helpful.
One of best plumbers in Nor Cal
Paul - Sacramento, CA
I have used Them more than once. Kevin is one of the best plumbers in the area. A little pricey, but he is excellent.
Nancy A - Sacramento, CA
What a pleasant surprise! Sean was able to come early, he explained everything in detail, he fixed the problem and the cost was much lower than I expected. He was very professional, and a very nice person to boot! I wouldn't hesitate to refer Crystal Blue to anyone needing a plumber. The next time we need help, I will call and request Sean! Thanks so much!
Enternal tankless code 14 unkown issue customer interested in Navien 240s
Sacramento California heating ac service AC repair Lennox pulse split system diagnostic Found furnace with a Good Vibration vibration coming from blower assembly most likely cause is blower motor bearings motor bearings leaking oil due to lack of maintenance motor has probably run dry of oil in bearings cause an abnormal wear and allowing for the vibration. Amp draw on motor 10.25 Max amp is 10 due to lack of oil motor is pulling higher amp then what it is supposed to this will cause motor to eventually overheat and shut down. Small amount of dust buildup on blower wheel recommend cleaning of blower wheel with replacement of new motor so to not be out of balance and cause new motor bearings to have shorter life expectancy. AC unit condenser Lennox Found bad capacitor 40 mfd reads 0.0 mfd outdoor fan capacitor 7 reads 7.1 good found low voltage wiring UV deteriorated showing copper wire on both common and hot 24 could cause short and burn out Transformer repaired low voltage wir
Technician will pull and reset existing toilet at mens restroom leaking at base price includes Parts labor and one year warranty leaks labor plus manufactures. Technician will collect credit card payment 5/917 Thursday
Unit 1 charge system replace, replace valve stem, replace electrical wire from disconnect to unit and capacitor Unit 2 replace electrical wire from disconnect to unit, replace the heat strip relay, replace capacitor and service valve refrigerant cap Unit 3 replace electrical wire from disconnect to unit and capacitor
Technician performed inspection from leak detection company blue tape on floor marking location of hot water copper supply line leak in slab. technician will need to jackhammer concrete excavate and expose copper line to braze with required fittings. Technician we'll put up plastic and then clothes work area to keep dust to a minimum the existing linoleum will need to be cut but not reinstalled customers responsibility once leak has been repaired contractor will wrap copper with protective 20 mil tape backfill compact then reinstall concrete price includes Parts labor and one year warranty leaks labor at repair only customer understands could take up to two days from start to finish but water line would be repaired and hot water restored Within the first day. Customer fully understands this quote is for this location marked out by leak detection company any other leaks would be additional.
Customer needs time to verify funding and will contact technician .
Replaced leaking pipe under the house. At 110 outlet under sink there's no power at Outlet. Cut open wall found leaky cast-iron 2-inch pipe which is seeping not to much, will have to cut pipe from under house and above floor to repair. Recommend hydro jetting all accessible drain lines from roof vents laundry bibs, leak in laundry room onto floor; recommend replacement of slow drain in master bathroom, recommend replacing P-trap cabling and hydro jetting that secondary line to resolve issue. Faucet leaks when turned on, recommend replacement
Reconnection of drain line and determine where secondary drain line goes
Unit 1 Capacitors compressor and outdoor fan 35 / 5 read 34.9 / 4.6 (recommend replacement) blower 7.5 reads 7.4 (good) Electrical wiring Wiring from disconnect to unit is to small for recommended amperage 10 awg wire should be 8 awg wire to be able to carry 50 amp circuit (recommend replacement) All other electrical tight connections no visual of overheating wires Amps for compressor 10.3 condenser fan motor .76 and blower motor 1.92 (good) Refrigerant pressures low recommend charging system to create proper Cooling for system to prevent compressor from overheating and to provide proper cooling temperatures inside oil on service port recommend replace valve stem most likely cause of refrigerant leak Unit 2 Capacitors compressor and outdoor fan 40 / 5 read 37.6 / 4.9 (recommend replacement) blower 15 reads 14.4 (good) Electrical wiring Wiring from disconnect to unit is to small for recommended amperage 10 awg wire should be 8 awg wire to be able to carry 50 amp circuit (rec
Customer to go over estimates with wife and make decision on which company to use for tankless water heater install
Estimate pre-approved to hook up existing 3 inch exhaust to water heater. At present see pics exhaust not hooked up going inside water closet. Contractor hook up exhaust only but not responsible for anything else water heater is too old for any kind of repairs needs replacement see estimate
Replacement of compressor, filter drier, pressure test, vac and recharge system Warranty 1 year parts and labor on all work performed
Diagnostic found capacitor and thermostat operationable compressor overheated inspection of system found system void of refrigerant cause of overheated compressor Repair options 1. Repair leak, pressure test ,vac and recharge system no guarantee that compressor is operationable due to being overheated and not able to test properly 2. Replace Refrigeration unit compressor and fan (condensing unit)
units operating normal at this time. No problems capacitors good Amp draws good Replaced air filters (2) 14x20x1 Found copper tubes rubbing against one another creating weak spot spread apart to stop the wear and prevent refrigerant leaks
Sacramento California heating AC repair / service Replacement of First Co drain pan do to pans being rusted and leaking water tested system for proper operation found plugged drain line due to being capped off improperly hooked up when sink was replaced will cause new drain pan to overflow and leak water causing water damage
Found drain pan bracket broke installed temporary brackets to hold pan up so unit could be operated. Proper repair will be replacement of drain pan
Replace drain pan and price for new grill Found drain pan rusted support brackets broke and holes in drain pan A previous improper repair was done a bunch of screws put in to try and hold pan up and a screwdriver wedged in unit misaligning unit and making unlevel. Return Grill pretty beat up / damaged Repairs needed installation of new drain pan, releveling of unit properly and new grill After replacement of drain pan and leveling of unit. tested drainage found drain lines not draining tried to clear restriction got back pressure looked for drain Outlet found capped off underneath sink. Needs drain line uncapped and connected to sink trap so system can drain
Perform drink clearing through clean Out back house. Technician will attempt to perform drain clearing customer States Greece in line. Customer understands there are no warranties on drain clearing
Removal of old part insulation of new part Replacement of part will have 1 year parts and labor warranty
2/16/17 Sean Unit 155 &154 crossover drain issue. $289.00 #154 unit has slow drain cause of problem grease will cable line with 100 machine. #253 unit second story blockage possible trap and sanitary tee will have to shop vac out sink to attempt to resolve issue. $289.00 Camera survey. Tuesday to determine issue with secondary line. Recommend: 1 1/2 copper repair in laundry room pipe feeds hot out from boiler.
Perform Work on previous estimate
Perform Work on previous estimate unit 1 managers office
Estimate to Auger toilet only price includes Parts labor with no warranty backups
Concrete excavation, tub and shower enclosure and valve single handle. Pex piping hot/cold, 40 gallon electric water heater. Customer to backfill and do concrete work and build wall for bathroom.
Perform Work on previous estimate unit 1 managers office