Crystal Blue Plumbing, Heating & Air provides heater and air conditioning repair, service, installation and services in Lincoln CA and surrounding areas. Check out what some of our customers are saying about Crystal Blue Plumbing, Heating & Air Plumbing, Heating and Air Conditioning services.
for Lincoln, CA
Exceeded expectations, again!!
Erickson - Lincoln, CA
Fantastic service and staff!! Continue with the professional work and exemplary customer service. Thanks Michael!!
Great Pricing, Fantastic Service and a Quick Turnaround!
MLE, Inc. - Lincoln, CA
Nice job. Quick
Darrin - Lincoln, CA
Needed to replace my moms water heater on short notice. Did it quickly and affordably while making the process easy
Debbi - Lincoln, CA
Mark - Lincoln, CA
Tom was very friendly. He replaced my shut off values to the kitchen faucet and put in new supply lines. He did a very good job.
Great service, Tom is an awesome man, and really knows his job!
Mike Conaty - Lincoln, CA
Tom did a great job replacing my kitchen faucet, he really saved me, He is also a very nice man, very friendly and really knows his job well
Great Professional Service
felicia - Lincoln, CA
I was having problems with my tankless hot water heater and Tom showed up and made me feel at ease. He assessed the situation and reassured me that he will do his absolute best. By the time he left, I had hot water again and couldn't have been happier! I am glad that I called Crystal Blue and will use them for any of my future needs with a shadow of a doubt.
Lincolnite - Lincoln, CA
I described my problem to 4 Lincoln plumbers before calling Crystal Blue because I try to stay local. Each said they had no idea how to deal with my situation. Sean arrived within an hour, and had it done less than 2 hours later.
Thank you Crystal Blue
Reid - Lincoln, CA
24:7 emergency line; friendly phone service; quick response to home; diagnosis and repairs done quickly and professionally. Great experience. Thank you so much Michael.
rosenda - Lincoln, CA
Estimate to perform drain clearing through closet flange after toilet removed. Job complete reset toilet check for leaks at customer inspect all okay. Customer understands there's no warranties on train clearing. While performing drain clearing customer running water at sink technician how to stop but water ran out from bathroom. Vacuumed up water dried it all up so customer. Customer stated she notice this morning minor water damage at hallway near bathroom and we also found water on master bath floor by shower.
Lincoln California heating ac service AC maintenance Goodman split system R22 refrigerant pressure 71 and 162 Super heat 8.5 subcool 19 meter device piston with current temperatures refrigerant pressure is good capacitor 50/5 reads 50.8 size 5.1 good Ampdraw compresser 14.7 actual 8.7 outdoor fan 1.8 actual 1.1 good Electrical connections found no loose connections all tight Contactor showing a little friction wear could cause contactor to get stuck in the on position
Extend water supply (Purified) under cabinet to three points for future connections. Convert un-filtered water line to hot and external along new cabinet to connect wash sink. Configure waste and water to set location for future sinks. Drains are 2" PVC along with just one set of hot/cold.
AC maintenance Vision inspection Found drain lines not connected properly - not sloped properly causing second trap water restriction furnace safeties not connected properly and furnace drain kinked not draining visual inspection of ductwork 12 inch duct supply collapsed internally restricting airflow Different 12-inch supply duct being pinched in trusses due to not being supported properly restricting airflow all other ductwork appears to be in working order no visual problems Capacitor 45 / 7.5 reads 45 / 7.6 good within mfg tolerance Contactor shows wear pitted little discoloration still making good contact at this time Amp draws compressor 16.14 reeds 8.14 outdoor fan motor .95 reads .77 amps good Removal of service cap to connect refrigerant gauges blackout little hip valve still leaking slightly Refrigerant pressures 100 on low 210 on high superheat 10 and subcool 19 outdoor temperature 55 degrees indoor temperature 69 degrees temp split 17 refrigerant readings appear
Existing water heater looks to be installed in 2004 or 2005 which puts the age of about 12 - 13 years old looks like yearly maintenance has not been performed. Turned faucets on in house water heater making intermittent crackling noises. Would highly recommend replacement for new efficient Bradford White Water Heater. Suspect tank holding sediment taking longer to heat water and running out of hot water sooner. Price includes Parts labor permit and one year warranty leaks labor plus manufactures. Water heater install complete estimate pre-approved and paid in full contractor will pull permit and drop off to customer with special instructions for smoke and CO detectors on day of inspection
Lincoln California heating AC Service glass repair water damage done from drain line getting punctured with screw. Replaced drain line due to existing one was already tripping on concrete not code
David Crosby lincoln
Estimate for water heater in lincoln