Crystal Blue Plumbing, Heating & Air provides heater and air conditioning repair, service, installation and services in Fair Oaks CA and surrounding areas. Check out what some of our customers are saying about Crystal Blue Plumbing, Heating & Air Plumbing, Heating and Air Conditioning services.
for Fair Oaks, CA
Morris - Fair Oaks, CA
Larry does Good job and is very friendly
Chuck - Fair Oaks, CA
Kevin was On Time, Professional and AWESOME!!! He did a great job identifying and fixing the problem quickly and professionally.
Responded quickly on a Saturday to clogged kitchen drain
Dave - Fair Oaks, CA
Very thorough, stayed with agreed cost even though project took much longer initially expected. Very courteous. I will use again, and recommend Crystal Blue!
Hard working, excellent people skills, quality job!
sheila - Fair Oaks, CA
What a great job! Tom and his crew were very pleasant to work with and took the time to fully understand the problem we had with an outdoor drain. They were thorough and cleaned up after solving the problem. I'd recommend Crystal blue Plumbing any time.
gustavo - Fair Oaks, CA
AC maintenance wires good no melting, burning or overheating, connections all tight Contactor contacts are in good shape little wear, coil no discoloration Capacitor 5 / 70 reads 5 /68.5 good still with mfg. tolerance Water washed condenser coil no charge part of maintenance Replaced air filter Amp draw condenser fan 1.26 reads 1.05 / compressor 25 reads 16 (Amps good) AC running with no problems at this time
Diagnostic on System visual inspection found bottom half of compressor Frozen covered in ice. Evap coil Frozen causing lack of air flow. Condenser fan motor with bad vibration. A wire inside of condenser fan motor section wrapped around condenser fan motor. Evap coil drain pan cracked/ broken Electrical fire in control compartment wire connections poorly taped for repair. Wires rubbing through copper due to sitting on them vibrating wearing through Clogged air filter restricting airflow helping to cause coil to freeze Diagnostic for problem ( why system is not cooling ) System is running blower motor, outdoor fan motor and compressor all turn on and start. Founf refrigerant pressure is low caused by Frozen evap coil and low refrigerant charge Repair to charge system to manufacturer's specifications to get system working / operationable at this time. This repair is not a long-term fix. Recommend other course of actions for long-term fix
Recommend for replacement due to age. Installed new InSinkErator Badger 5 half horsepower garbage disposal reinstall Plumbing load tested no leaks all okay price includes Parts labor and one year warranty leaks labor plus manufacturers after checking all for leaks existing faucet supply line cold side has defective supply line recommend full replacement of faucet. Tightened up for customer no leak at this time but there will be no warranty on supply line cold side faucet
Fair oaks cleared a sewerline
Tankless water heater repair. Fair oaks plumbing. Fair oaks.
Plumbing repairs. Sewer line replacement. Fair oaks
Fair Oaks California heating ac service Amana / Goodman furnace and AC condenser water dripping from unit caused by plug drain line found plugged air filter and dirty blower motor and blower wheel evap coil clean unplug drain line flushed sediment build-up out washed blower motor wheel and housing
Plumbing leaks. Plumbing repairs. Fair Oaks plumbing. Fair Oaks.
Water heater replacement. Fair oaks plumbing. Fair oak.
Shower repairs. Fair oaks plumbing. Fair oaks
Hose bibs leaking. Fair Oaks plumbers. Fair Oaks
Fair Oaks toilet replacement