Crystal Blue Plumbing, Heating & Air provides heater and air conditioning repair, service, installation and services in Antelope CA and surrounding areas. Check out what some of our customers are saying about Crystal Blue Plumbing, Heating & Air Plumbing, Heating and Air Conditioning services.
for Antelope, CA
check water leak
Scheffler - Antelope, CA
Chelsea - Antelope, CA
Not only did I save money, but I received fast service from knowledgeable people. I called another company that I had used before and they made me wait 2 hours before telling me they couldn't help me. So when I called Crystal Blue and spoke to someone right away I was impressed. I will use them for everything in the future.
Excellent Customer Service
Ms. Angel - Antelope, CA
I have had 3 technician's out to my home thus far and each one was courteous, efficient and so friendly. It's been a long time since I have received service on this level.
Tiffany - Antelope, CA
Our AC unit went out when it was 104 degrees. Jordan was out the next day hours early and had us up and running in 10 minutes!
AC Trouble Call
Terrance - Antelope, CA
Michael, provided OUTSTANDING service, his customer rapport is truly professional. He responded in a timely manner with consideration to our time and was extremely courteous. A customer oriented technician of the highest caliber. mm
Outstanding service, exceeded my expectations
Kelley - Antelope, CA
Done same day
Jennifer - Antelope, CA
ay - Antelope, CA
Great communication great customer service and fast install
Lucy - Antelope, CA
friendly and good service
Antelope California heating AC service AC maintenance AC diagnostic AC not working no cool air AC diagnostic findings system trying to run / cool not working house is 87Â° inspection at outdoor unit found compressor overheated Open winding terminals. outdoor fan running has very bad vibration. causing top panel to start cracking will continue to damage top that is holding fan motor in place due to vibration. capacitors found bad compressor capacitor likely cause of compressor overheating do to system trying to run and not working possible damage to compressor has occurred. Repairs needed compressor called off to try and see if windings will open if windings do not open compressor will need to be replaced if windings open next step would be to replace capacitor. Replacement of capacitor needed to be able to test system operation. Cooled compressor down replaced capacitor turned on system checked operation blower capacitor still weak could go out at anytime and keep the blowe
Antelope California heating ac service AC maintenance Lennox package unit Electrical connections all tight no broken, burnt or overheating terminals. Electrical wire for condenser fan becoming brittle starting to crack capacitors compressor 35 reads 34.3 , outdoor fan 7.5 reads 7.5 , blower 7 reads 7.3 (good) Amp draw compressor 18.2 actual 14.28 , outdoor fan 2.8 actual 1.13 , blower 2.3 actual 2.14 (good) Refrigerant pressure is good Performed simple water wash on condenser coil as part of AC maintenance flushed drain line of sediment build up Blower
Heating and air conditioning maintenance plan heating maintenance
Water heater repairs. Antelope plumbing.